Are you planning a data center for your customer?
We provide you with the tender documents for the entire technical
infrastructure for the construction of a server room or data center.
IT-SECURITY ROOM - ACCESS DOOR
Delivery and installation of an access door as a single door system.
The door hinge is to be DIN right or left.
Technical requirements for the door system:
- fire resistance min. F120
- smoke gas tightness according to DIN 18095 tested as system test
- fire water tightness according to EN60529 tested as system test
- min. IP54 - burglary protection WK IV according to EN1627 for the door system
Furthermore, the door system must be designed to resist pressure build-up
and mechanical attacks. Corresponding verifications are to be provided.
Electric lock in accordance with EN 1300 prepared for activation by an access
control system provided by the customer, as well as potential-free contacts for
monitoring the door.
Surface treatment of the access door: Steel parts galvanized and primed.
The final painting is done in RAL / color according to the client.
Minimum dimensions (clear passage dimensions) / clear passage dimensions
(required, to be entered by the bidder)
Width: 1000 mm, height: 2100 mm, door leaf thickness: 60 mm
Installation drawings and the door construction must
be enclosed with the bid.
We will be pleased to support you with our know-how, even if it concerns
parts of IT security components.